On this project we replaced the existing load side bus bar of the generator breaker. The existing bus bar would only accept a maximum of 6 cables. We made new bar that would accommodate 8 cables. When designing the new bus bar the center phase was extended down to make terminating the cables easier for the contractor. The neutral was also modified to accept more cables and to install the new neutral CT. This completed the last of the 3 generators that we have done for Dayton Children’s over the past 2 years.